Certified Projects Database
||RMI Basalt Innovation Center
||JE Dunn Construction
||Mechanical Systems Designer
|Energy Star Rating
||Heating Degree Days
||Cooling Degree Days
- PHIUS+ Source Zero
||December 21, 2015
||Structurally Insulated Panels (SIPs) - R50
||Exposed concrete slab on grade (lower level) with R20 continuous insulation, cross laminated timber (upper level).
||Structurally Insulated Panels (SIPs) - R67.
||Schuco FW50+ SI for fixe windows (Uf = 0.381). AWS 102 for motorized operable casement windows (Uf = 0.713).
||Alpen QuadPane C180, C272, C366 - with 2 HM 88 films, 90% krypton fill and low iron glass. Glazing tuned per aspect. Center of glazing U-value 0.075 to 0.078.
||Two dedicated outdoor air ventilation units with demand control ventilation, oversized ducts, high efficiency filters. 0.25 inches external static pressure. 80% heat recovery effectiveness. Tempeff RGSP 2700 and 600.
||Hyperchair direct occupant heating, electric resistance backup.
||0.3 ACH@50 Pa
||No mechanical cooling. Natural ventilation, night flush, ceiling, desk and Hyperchair fans to extend thermal comfort range.
||Architectural Applications (high performance design). Greenhammer (infiltration), Pie Consulting Engineers (Air tightness testing)
||This building will be net positive through onsite PV.